Current Region: Global (EN)
This site uses some unobtrusive cookies to store information on your computer. By using the website, you hereby agree on cookies storage.
SHA Series Modular Desiccant Air Dryers are ideal for point of use, laboratories and confined areas. They provide a continuous supply of dry compressed air by automatically cycling the flow of air through two desiccant beds.
Pneumatic Products’ SHA Series Modular Desiccant Air Dryers protect moisture sensitive applications requiring low pressure dew points. Delivers dew points of ISO 8573-1: 2010 Class 1 (-94°F, -70°C) and Class 2 (-40°F, -40°C) with flow rates of 7 to 40 scfm (12 to 68 nm3/h). Critical applications include labs, hospitals, pharmaceutical manufacturing and other high-tech installations.
The SHA Series incorporate a time proven design, with superior features and reliability, in a compact and easy to install package. Standard features include:
Compressed air enters the dryer and is directed to Tower 1 by valve (A), and then to the dryer outlet through shuttle valve (B). A portion of the dried air is throttled to near atmospheric pressure by means of orifice (C). This extremely dry, low-pressure air flows through and regenerates the desiccant in Tower 2 and is exhausted through purge/repressurization valve (D) and exhaust muffler (E) to atmosphere. After a set time, the automatic solid state timer closes purge/repressurization valve (D) allowing Tower 2 to repressurize slowly. At the end of 2 minutes, valve (A) shifts and purge/ repressurization valve (D) reopens. The main air flow is now dried by Tower 2 while Tower 1 is being regenerated.
|Model||INLET FLOW RATING1
1 Inlet flows are established in accordance with CAGI (Compressed Air and Gas Institute) standard ADF-200, Dual Stage Regenerative Desiccant Compressed Air Dryers - Methods for Testing and Rating. Conditions for rating dryers are: inlet pressure - 100 psig (7 kg/cm2); inlet temperature - saturated at 100°F (38°C).
2 Average Purge Flow is the total amount of air used to purge and repressurize off-stream towers averaged over the cycle time. Maximum Purge Flow is the flow rate through the off-stream tower during that portion of the cycle the purge/ repressurization valve is open.
CAPACITY CORRECTION FACTORS